||FYI||*****(STANDARD COMMENT) This project is: Kaiser Permanente, 215 S Parkside Dr, Suite 100:
Date of Plans: 5.16.14
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.
|FYI||(STANDARD COMMENT) IMPACT TO EXITING AND/OR FIRE PROTECTION SYSTEMS
Egress components and fire protection systems that may be negatively impacted by yoru scope of work will be required to comply with the currently adopted fire code. As an example, if your work increases the occupant load of a space, the existing egress components will be required to comply with the requirements of the new occupant load.|
|Attention||*****(STANDARD COMMENT) RED-LINED COMMENTS
The following RED-LINED items are to be corrected prior to final inspection:
1. Sheet A6.4 detail 4: above ceiling sprinkelrs needed at the ACT/Wood transition OR physical barrier must be provided.
2. Plastic wall panels shall meet interior finish requirements of the 2009 IFC/IBC. reference sheet A10.0
|Attention||(STANDARD COMMENT) CONSTRUCTION SPLICES
You are strongly encouraged to have any splices that may occur during this project, reviewed by CSFD. Failure to do so, can result in coordination issues that could prevent a final inspection from being completed, thus delaying the issuance of a Certificate of Occupancy.
|FYI||(STANDARD COMMENT) INTERIOR FINISH:
Interior finish, to include wall coverings and window treatments shall comply with Table 803.3 of the 2009 IFC/IBC.
Reference Sheet A10.0 plastic wall panels.|
|Attention||(STANDARD COMMENT) FIRE EXTINGUISHERS
PLAN REVIEWS DO NOT INCLUDE REVIEW OF TYPE, SIZE OR PLACEMENT OF FIRE EXTINGUISHERS.
|FYI||*****(STANDARD COMMENT) KNOX (TM) ENTRY FOR NEW BUILDINGS
KNOX (TM) ---XXX---Box is required at this location.
It is recommended that all KNOX (TM) boxes be placed in a highly accessible location approximately 10 feet off of the ground, and usually placed near the front entrance to the building.
KNOX (TM) Security Equipment is the only approved type, and must be ordered directly through the CSFD Division of the Fire Marshal at 2880 International Circle, Suite 200-7, or by calling (719) 385-5982.
***************ALLOW AT LEAST 4 WEEKS DELIVERY TIME *************************
YOUR FINAL WILL NOT BE APPROVED WITHOUT THE KNOX SECURITY EQUIPMENT INSTALLED! YOU MUST ALSO CONTACT OUR OFFICE AT LEAST 1 WEEK PRIOR TO YOUR REQUEST FOR FIRE FINALS TO ARRANGE FOR A CSFD FIRE INSPECTOR TO MEET YOU AT THE SITE TO INSTALL PROPER KEYS FOR THE BUILDING INTO THE KNOX SECURITY UNIT.
|FYI||(STANDARD COMMENT) EXIT SIGNS AND EMERGENCY LIGHTING:
Exit Signs and Emergency Lighting shall be in compliance with the adopted building and fire code.
Paths of egress will be verified to be compliant, even if they are beyond the scope of work. If your scope of work impacts the means of egress, i.e. a new conference room - the path of egress beyond that scope of work will be verified to make sure occupants can safely egress the building.|
|FYI||(STANDARD COMMENT) LOCKING HARDWARE:
All locking and latching devices shall comply with the requirements of the adopted building and fire code.|
|FYI||*****(STANDARD COMMENT) FIRE PROTECTION SYSTEMS
The following systems are present or required in this facility:
--XXX---Fire Alarm System
--XXX---Water-Based Suppression System (fire sprinklers, standpipes, etc)
Applicable Fire Protection System plans shall be submitted to the CSFD Construction Services office in the Regional Development Center.
|FYI||(STANDARD COMMENT 10) INSPECTIONS
Due to the dynamic nature of inspectors schedules, PLEASE call your inspection requests in with ample time to allow scheduling.
Please call 719-385-5982 Extension 2 to schedule all construction related inspection activities.
When calling, please have your complete CSFD plan review number(s) ready for each inspection request.
( i.e. 20001234 - HM -2 or 20000012 - CN - 1)
The CSFD Approved sets of plans are to be on site for all inspections.|
|FYI||(STANDARD COMMENT) REVIEWS
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirements are met as established by the Authority Having Jurisdiction, whether or not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the adopted fire code requirements, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.
|FYI||(STANDARD COMMENT) PERMITS
Insure all applicable permits are obtained from the Regional Building Department and the Colorado Springs Fire Department for the work that is being done at this site.