NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
03310 FILLMORE RIDGE HTS
||FYI||CRDN, 3310 Fillmore Ridge Hts: interior remodel - change of occupancy
CN:Code: 09 IBC - 09 IFC - 11 PPRBC /Class:F1 / Const: II-B /Stories:1/Size: /OL: 418100
date of plans: 5/6/14
TEXTILE RESTORATION FACILITY
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.
The storage, use and/or dispensing of hazardous materials within this facility shall be in accordance with all applicable provisions of the 2009 International Fire Code, as amended, including (but not limited to) Chapters: Hazardous Materials 27, Corrosives 31, Compressed gases 30, Flammable & Combustible Liquids 34.
ATTENTION: See our web site for our latest fire department plan review comments. From the Pikes Peak Regional Building Department web site (www.pprbd.org), select "RELATED WEB SITES" in the upper right corner. Click on Colorado Springs FIRE PREVENTION. Then select PLAN REVIEW STATUS, click VIEW PLAN REVIEW STATUS. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.|
|Approved||NO ANNUAL PERMIT REQUIRED BASED ON REPORTED MATERIALS AND QUANTITIES
NO CONSTRUCTION PERMIT REQUIRED.
|FYI||CHEMICAL INVENTORY, AS DECLARED
SEE ELECTRONIC DOCUMENTS
OPERATIONS PLAN DESCRIPTION --- SEE ELECTRONIC DOCUMENTS
THIS IS A TEXTILE RESTORATION COMPANY; CLEANS TEXTILES PRODUCTS SUCH AS, RUGS, CLOTHING, CURTAINS ETC. USED FOLLOWING FIRE, FLOODING ETC.
small amount of detergent: three, 13 gallon liquid containers:
Viva Soft, Viva Oxy, Viva Oleo = OHH/IRR
These materials/hazard classes DO NOT exceed the maximum allowable quantities per control area as defined by 2009 IFC Table 2703.1.1(1) - (4) for OHH in a non sprinklered area.
These materials/hazard classes DO NOT exceed the Hazardous Materials Permit Thresholds as defined in IFC Tables 105.6.20, 105.6.20, 105.6.8, 105.6.10
The General Requirements of 2009 IFC Sections 2701, 2703 and 3401 and shall apply for the use and storage of these materials.
NO ANNUAL HAZARDOUS MATERIALS OPERATIONAL PERMIT IS REQUIRED FOR THIS FACILITY AT THIS TIME.
ATTENTION: THIS FACILITY USES HYDROXYL GENERATORS (TWO) WHICH ELIMINATE ODORS AND PATHOGENS. UV IRRADIATION TECHNOLOGY. "ODOROX" MACHINES.
|Attention||This facility DOES NOT exceed the annual operational permit amount for a Hazardous Materials Permit. No Permit is required at this time.
APPLICATION FOR PERMIT IS FOUND AT
IN THE CSFD HAMMERS ON LINE PERMIT PROGRAM @ https://hammers.springsgov.com/submit
This is required to be completed prior to the hazardous materials construction final. The permit is automatically renewed annually and includes a permit inspection and associated permit fee.
If you have any questions please contact the Division of the Fire Marshal @ 719 385-5978.|
|FYI||IFC 2009, AS AMENDED, CHAP 27
Quantities not exceeding the maximum allowable quantity per control area. The storage, use and handling of
hazardous materials in quantities not exceeding the maximum allowable quantity per control area indicated in Tables 2703.1.1(4) through 2703.1.1(4) shall be in accordance with Sections 2701 and 2703.
CHAPTER 12 DRY CLEANING
THIS FACILITY IS NOT A DRY CLEANING FACILITY. NO SOLVENTS. EXEMPT FROM CHAPTER 12.
Incompatible materials in storage and storage of materials that are incompatible with materials in use shall be separated when the stored materials are in containers having a capacity of more than 5 pounds or 0.5 gallon. Separation shall be accomplished by:
1. Segregating incompatible materials in storage by a distance of not less than 20 feet.
2. Isolating incompatible materials in storage by a noncombustible partition extending not less than 18
inches above and to the sides of the stored material.
3. Storing liquid and solid materials in hazardous material storage cabinets.
4. Storing compressed gases in gas cabinets or exhausted enclosures in accordance with IFC 2009 Sections 2703.8.5 and 2703.8.6. Materials that are incompatible shall not be stored within the same cabinet or exhausted enclosure.|
|FYI||HAZARDOUS MATERIALS STORAGE CABINETS
Where storage cabinets are used to increase maximum allowable quantity per control area or to comply with chapter 27, such cabinets shall be in accordance with IFC 2009, as amended, Sections 2703.8.7.1 and 2703.8.7.2.
The interior of cabinets shall be treated, coated or constructed of materials that are nonreactive with the hazardous material stored. Such treatment, coating or construction shall include the entire interior of the cabinet. Cabinets shall either be listed in accordance with UL 1275 as suitable for the intended storage or constructed in accordance with the following:
1. Cabinets shall be of steel having a thickness of not less than 0.0478 inch (1.2 mm) (No. 18 gage). The cabinet, including the door, shall be double walled with a 11/2-inch (38 mm) airspace between the walls. Joints shall be riveted or welded and shall be tight fitting. Doors shall be well fitted, self-closing and equipped with a self-latching device.
2. The bottoms of cabinets utilized for the storage of liquids shall be liquid tight to a minimum height of 2 inches (51 mm).
Electrical equipment and devices within cabinets used for the storage of hazardous gases or liquids shall be in accordance with NFPA 70.
Cabinets shall be clearly identified in an approved manner with red letters on a contrasting background to read: HAZARDOUS-KEEP FIRE AWAY.|
|FYI||LIMIT CONTROLS AND VENTILATION
Indoor storage areas and storage buildings shall be provided with mechanical exhaust ventilation or natural ventilation where natural ventilation can be shown to be acceptable for the materials as stored.
*** Ventilation shall be in accordance with the International Mechanical Code and PPRBD Mechanical Dept.|
|FYI||General precautions for the safe storage, handling or care of hazardous materials shall be in accordance with the IFC 2009, as amended, Sections 2703.9.1 through 2703.9.9.
- Personnel training and written procedures.
- Fire department liaison.
- Protection from vehicles.
- Electrical wiring and equipment. Electrical wiring and equipment shall be installed and maintained in
accordance with the ICC Electrical Code.
- Static accumulation.
- Protection from light.
- Shock padding.
|FYI||Labeling - An NFPA 704 compliant Hazard Placard is required for each pedestrian entry door rooms containing hazardous materials in excess of the exempt amounts (this door could be interior or exterior) and all such doors shall be included. The minimum size of the Hazard Placard shall be 15" by 15". This requirement is subject to verification at the time of the Hazardous materials Inspection prior to signing the Fire Final.
*** Refer to the product MSDS for NFPA 704 hazard ratings
Markings. Individual containers, cartons or packages shall be conspicuously marked or labeled in an
****ATTENTION: ALL PIPING, SYSTEM, AND CONTAINER LABELING, SIGNAGE, PLACARDING SHALL BE IN PLACE/POSTED/ADHERED AT THE TIME OF INSPECTION.|
|FYI||Piping, tubing, valves, fittings and related components used for hazardous
materials shall be in accordance with the following:
1. Piping, tubing, valves, fittings and related components shall be designed and fabricated from
materials compatible with the material to be contained and shall be of adequate strength and durability to
withstand the pressure, structural and seismic stress, and exposure to which they are subject.
2. Piping and tubing shall be identified in accordance with ANSI A13.1 to indicate the material conveyed.|
|FYI||Equipment, machinery, and required detection and alarm systems associated with the use, storage, or handling of hazardous materials shall be listed or approved. This requirement is subject to verification at the time of the Hazardous materials Inspection prior to signing the Fire Final.|
|FYI||CONTRACTOR: Prior to scheduling the Fire Final please contact the Hazardous Materials Inspector to arrange a Hazardous Materials Inspection prior to final signature being provided.
OWNER/CONTRACTOR: Contact the CSFD Office of the Fire Marshal at 719-385-5978 to schedule the hazardous materials construction inspection(s).|
Material Safety Data Sheets (MSDS) for all hazardous materials shall be either readily available on the premises as a paper copy, or where approved, shall be permitted to be readily retrievable by electronic access. Approved electronic access shall be as follows:
1. Media shall be USB Flash Drive.
2. Format shall be Microsoft Word 2000 or newer docu-ment, PDF, or other approved format.
Where a Knox Box is located at a facility, one USB de-vice shall be stored in the Knox Box and one device shall be located in an approved location(s). All devices and content shall be maintained.|