||FYI||*****(STANDARD COMMENT 1) This project is: Calhan School, 800 Bulldog Dr:
This plan review is based on the requirements found within the adopted Editions of the International Building Code, International Fire Code and the related Standards.|
|FYI||*****(STANDARD COMMENT 5) DESIGNER/INSTALLER INFORMATION
Fire Alarm system was designed by: CSSC
Fire alarm system is being installed by: MEISNER ELECTRIC
|FYI||(STANDARD COMMENT) ADDITIONS AND REMODELS TO EXISTING SYSTEMS:
Existing systems shall comply with current codes and standards for all areas occupied by the tenant, not just the area of remodel. (CSFD Administrative Ruling 2010-2)|
|FYI||*****(STANDARD COMMENT 7) Scope of Work: REPLACEMENT OF EXISTING NOTIFICATION WITH SYNCHABLE APPLIANCES
|FYI||(STANDARD COMMENT) RECORD OF COMPLETION:
The Record of Completion (ROC) shall be filled out in accordance with 10.18.2 for new installations.
All modifications made after the initial installation shall be recorded on a revised Record of Completion. All changes shall be shown and the revised ROC and shall include a revision date.
|FYI||(STANDARD COMMENT) PRE-TEST REQUIREMENT:
Before requesting final approval of the installation, the installing contractor shall furnish a written statement that the system has been installed in accordance with approved plans and testing in accordance with the manufacturer's published instructions and the appropriate NFPA requirements. (10.18.1.3)
CSFD requires a 100% pre-test - Evidence may be documented on the Record of Completion.|
|FYI||(STANDARD COMMENT) ACCEPTANCE TESTING:
At the time of this inspection the Fire Inspector will expect ALL devices involved in this fire alarm project to be tested. The installer should be aware of the fact that in a larger facility there may by a need to isolate the fire alarm system to only the area being tested. The alarm installer is to insure that building owner and/or manager and the General Contractor has been informed of the test criteria, time and date of the test, and have given their approval.
Acceptance testing shall be completed in accordance with Chapter 14 of NFPA 72|
|FYI||(STANDARD COMMENT 12) STATE PROJECTS ROUGH-IN PERMIT AND INSPECTIONS:
All Fire Alarm systems wiring installed within the City of Colorado Springs must be inspected by the State Electrical Inspector PRIOR TO the Fire Final on the system. The State Electrical Inspector shall sign in the appropriate space on the CSFD permit card that the rough-inspection has been done and approved.|
|FYI||(STANDARD COMMENT 10) INSPECTIONS
Due to the dynamic nature of inspectors schedules, PLEASE call your inspection requests in with ample time to allow scheduling.
Please call 719-385-5982 Extension 2 to schedule all construction related inspection activities.
When calling, please have your complete CSFD plan review number(s) ready for each inspection request.
( i.e. 20001234 - HM -2 or 20000012 - CN - 1)
The CSFD Approved sets of plans are to be on site for all inspections.|
|FYI||(STANDARD COMMENT 19) PLAN REVIEW/PERMIT FEES
All fire department fees are to be paid prior to issuance of any permits. These fees must be paid directly to the Colorado Springs Fire Department - Development Review Enterprise - at 2880 International Circle - Suite 200-7.|
|FYI||(STANDARD COMMENT) REVIEWS:
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirement are met as established by the Authority Having Jurisdiction, whether of not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the fire code requirements of the adopted International Fire Code, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.
|FYI||(STANDARD COMMENT) DEW REVIEWER CONTACT:
If you have any specific questions or concerns about these comments, please feel free to contact me at:
Doreen "Dee" Withee, CFPS
Fire Protection Engineer II, CSFD
2880 International Circle, Suite 200-7
Colorado Springs, CO 80910
(T) 719-385-7361 / (F) 719-385-7330