||FYI||*****(STANDARD COMMENT 1) This project is: Aeroflex, 5030 Centennial Bl: interior remodel
This plan review is based on the requirements found within the adopted Editions of the International Building Code, International Fire Code and the related Standards.|
|FYI||*****(STANDARD COMMENT 5) DESIGNER/INSTALLER INFORMATION
Fire Alarm system was designed by: SIMPLEXGRINNELL
Fire alarm system is being installed by: SAME
|FYI||*****(STANDARD COMMENT 7) Scope of Work: CONVERT EXISTING SYSTEM TO WATERFLOW ALARM - MINIMUM REQUIRED
|Approved/Corrected||*****(STANDARD COMMENT 8) The following RED-LINED items are to be corrected prior to final inspection:
1. Delay in AC power loss reporting shall be 2 hours.
2. Please note - waterflow alarm systems do not have evacaution tones as their intent is to supervise the status of the fire sprinkler system.
Off-site monitoring of this fire alarm system is required and shall be provided by an approved monitoring agency.
The phone number to be used to report a fire emergency is (719) 444-7632.
|FYI||(STANDARD COMMENT 13) LICENSED INSTALLER/SERVICE TECHNICIAN
An On-Site Installer/Service Technicial shall supervise all on-site work on any fire protection system. This On-Site Installer shall have a current Installer Certificate (RBD Wallet Card), on his/her person, while on the job site.|
|FYI||(STANDARD COMMENT) RECORD OF COMPLETION:
The Record of Completion (ROC) shall be filled out in accordance with 10.18.2 for new installations.
All modifications made after the initial installation shall be recorded on a revised Record of Completion. All changes shall be shown and the revised ROC and shall include a revision date.
|FYI||(STANDARD COMMENT) REACCEPTANCE TESTING:
Reacceptance testing shall be completed in accordance with Chapter 14 of NFPA 72
|Attention||(STANDARD COMMENT 11) ROUGH-IN PERMIT AND INSPECTIONS:
All Fire Alarm systems wiring installed within the City of Colorado Springs must be inspected by the Pikes Peak Regional Building Department PRIOR TO the Fire Final on the system. This will require the installing contractor to obtain a Rough-In Permit issued by the Regional Building Department. Please call RBD at 327-2880 for additional information on how to obtain this permit.|
|FYI||(STANDARD COMMENT 10) INSPECTIONS
Due to the dynamic nature of inspectors schedules, PLEASE call your inspection requests in with ample time to allow scheduling.
Please call 719-385-5982 Extension 2 to schedule all construction related inspection activities.
When calling, please have your complete CSFD plan review number(s) ready for each inspection request.
( i.e. 20001234 - HM -2 or 20000012 - CN - 1)
The CSFD Approved sets of plans are to be on site for all inspections.|
|FYI||(STANDARD COMMENT 19) PLAN REVIEW/PERMIT FEES
All fire department fees are to be paid prior to issuance of any permits. These fees must be paid directly to the Colorado Springs Fire Department - Development Review Enterprise - at 2880 International Circle - Suite 200-7.|
|FYI||(STANDARD COMMENT) REVIEWS:
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirement are met as established by the Authority Having Jurisdiction, whether of not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the fire code requirements of the adopted International Fire Code, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.
|FYI||(STANDARD COMMENT) DEW REVIEWER CONTACT:
If you have any specific questions or concerns about these comments, please feel free to contact me at:
Doreen "Dee" Withee, CFPS
Fire Protection Engineer II, CSFD
2880 International Circle, Suite 200-7
Colorado Springs, CO 80910
(T) 719-385-7361 / (F) 719-385-7330