NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
THE 64 STORE
03512 TEJON ST
deficient plan submittal
Extraction Tek: Matthew
send additional information on ETL listing; request send full ETL report to plan reviewer (via email)
Per matthew Water heater is not Listed; will be 3 ft AFF and 10 ft away from extraction machine in same room. " This is the alternative design that will address a non listed device in a hazardous occupancy"
Heater heats the water bath at the collector
Sent plan reviewer the process description also.
Matthew and Mark
UL 73 tested to.
Ben Parsay: Architect:
Plan reviewer question on heater on plans?
Not supposed to be there per Mr. Parsay; comment reference K Yeager? doesn't know
Is this a classified occupancy ? No per Parsay
K: Class I Div 2 required; Parsay states ventilation mitigates hazard occupancy class per NEC. Mr Parsay to send K standard/code reference that allows.
Mr. Parsay states two 100 lb butane cylinders exterior storage.
request: PID gas detection spec/cut sheets (listed required and sensor info) Parsay to send to Plan reviewer
Jeff of MariCare: manager
No piping to extraction room: told that butane can't be piped--generates heat and requires additonal engineering and components. Piping should not be on plans
Wanted to "mix" butane gas on site exterior of building (Jeff did not want to do mixing)
K:Not advised; not allowed. Have a qualified gas supplier supply gas.
Jeff: will have 20 lb cylinder in room for supply only and will store additional butane in cage exterior.
Kay: resubmit plans with revisions: no piping, chemical inventory amounts of butane, storage amounts and locations and use amounts and locations. No heater ? per parsay
K: Have plans revised current and resubmit to plan reviewer; plans need to be resubmitted through all depts.
disapproved plans I have them at FDC. let me know I will route to RBD
K send (plan reviewer) a narrative detailing butane use, storage etc. and process.
Jeff to send info to K