NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
CENTURY COMMUNITIES CLAREMONT RANCH
02516 SHANNARA GRV
||FYI||*****(STANDARD COMMENT) This project is: Century Communities, Claremont Ranch, 2516 Shannara Grv:
Date of Plans: 5.6.14
BE ADVISED - REVIEW DOES NOT INCLUDE ACCESS OR WATER SUPPLIES
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.
|Attention||(STANDARD COMMENT) CONSTRUCTION SPLICES
You are strongly encouraged to have any splices that may occur during this project, reviewed by CSFD. Failure to do so, can result in coordination issues that could prevent a final inspection from being completed, thus delaying the issuance of a Certificate of Occupancy.
|FYI||(STANDARD COMMENT) FIRE EXTINGUISHERS - MULTI-FAMILY RESIDENTIAL OCCUPANCIES
OPTION #1 -- Install 2A-10B:C fire extinguishers at a rate of 1 unit per 3000 squre feet, AND a maximum of 75-ft travel distance. These extinguishers are to be located in the common areas of the complex. History shows they are often stolen, therefore option 2 is highly recommend.
OPTION #2 -- Install (1) 1A-10B:C ext. in each apartment/town home. It's ok to hang under a kitchen sink, in a closet, or in an ATTACHED garage, just remember to make sure it's accessible
Install extinguishers in highly visible and accessible locations, never in a dead-end area, and always try to place them near an exit pathway or at an exit(s). Mount 4" off floor to a maximum of 5 ft. to the top of the fire ext. (HINT: About waist high is perfect.) "FIRE EXTINGUISHER" signs may need to be posted too properly identify where the units are located if they're not highly visible.
|FYI||(STANDARD COMMENT) ADDRESSING
Address shall be posted on street addressed side of structure. Minimum 5" numbers with 1/2" stroke. Contrasting color to background. (2009 IFC 505.1)|
|FYI||*****(STANDARD COMMENT) FIRE PROTECTION SYSTEMS
The following systems are present or required in this facility:
-----Fire Alarm System
--XXX---Water-Based Suppression System (fire sprinklers, standpipes, etc)
Applicable Fire Protection System plans shall be submitted to the CSFD Construction Services office in the Regional Development Center.
|FYI||(STANDARD COMMENT) FIRE PROTECTION SYSTEM PLANS NOT REVIEWED
There were fire protection system plans attached to the construction plans, however, they were not reviewed due to lack of specification sheets, calculations, etc. The sub-contractors for these systems must submit these plans for our review, and obtain separate permits from the CSFD for the installation of said systems. No work is allowed to begin without proper permits.
|FYI||(STANDARD COMMENT 10) INSPECTIONS
Due to the dynamic nature of inspectors schedules, PLEASE call your inspection requests in with ample time to allow scheduling.
Please call 719-385-5982 Extension 2 to schedule all construction related inspection activities.
When calling, please have your complete CSFD plan review number(s) ready for each inspection request.
( i.e. 20001234 - HM -2 or 20000012 - CN - 1)
The CSFD Approved sets of plans are to be on site for all inspections.|
|FYI||(STANDARD COMMENT) REVIEWS
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirements are met as established by the Authority Having Jurisdiction, whether or not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the adopted fire code requirements, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.
|FYI||(STANDARD COMMENT) PERMITS
Insure all applicable permits are obtained from the Regional Building Department and the Colorado Springs Fire Department for the work that is being done at this site.