||FYI||*****(STANDARD COMMENT 1) This project is: Bingo Burger, 132 N Tejon St:
This plan review is based on the requirements found within the adopted Editions of the International Building Code, International Fire Code and the related Standards.|
|FYI||*****(STANDARD COMMENT) The special hazard suppression system is being installed by: SIMPLEXGRINNELL
|FYI||*****(STANDARD COMMENT) DESIGN:
Type of System: WET CHEMICAL, ANSUL R102
Size of System: 6 GALLONS USING 19 OF 22 AVAILABLE FLOW POINTS
Hazard Protected: GRIDDLES, FRYERS|
|FYI||(STANDARD COMMENT 5) INDICATION OF SYSTEM ACTIVATION:
An audible OR visual indication shall be provided that the system has operated, that personnel response is needed, and that the system is inneed of recharge.
|FYI||(STANDARD COMMENT 6) FIRE ALARM SYSTEM CONNNECTIONS:
The extinguishing system shall be connected to the fire alarm system, if provided, in accordance with NFPA 72.
|FYI||(STANDARD COMMENT) LICENSED INSTALLER/SERVICE TECHNICIAN
An On-Site Installer/Service Technicial shall supervise all on-site work on any fire protection system. This On-Site Installer shall have a current Installer Certificate (RBD Wallet Card), on his/her person, while on the job site. |
|FYI||(STANDARD COMMENT 8) CERTIFICATE OF INSTALLATION:
It is the installer's responsibility to certify through this form that the system has been properly installed and tested.
The form is to be filled out in its entirety PRIOR TO THE ARRIVAL OF THE FIRE INSPECTOR that is conducting the final inspection and/or the acceptance test of the system.
FINAL INSPECITONS WILL NOT BE CONDUCTED WITHOUT THIS FORM BEING COMPLETED.
|FYI||(STANDARD COMMENT 9) MANUFACTURER'S DATA
The approved set of system plans, manufacture's product data sheets on all equipment being installed, and the installation permit are to be on site for all fire department inspections. |
|FYI||(STANDARD COMMENT 10) INSPECTIONS
Due to the dynamic nature of inspectors schedules, PLEASE call your inspection requests in with ample time to allow scheduling.
Please call 719-385-5982 Extension 2 to schedule all construction related inspection activities.
When calling, please have your complete CSFD plan review number(s) ready for each inspection request.
( i.e. 20001234 - HM -2 or 20000012 - CN - 1)
The CSFD Approved sets of plans are to be on site for all inspections.|
|FYI||(STANDARD COMMENT 15) PLAN REVIEW/PERMIT FEES
All fire department fees are to be paid prior to issuance of any permits. These fees must be paid directly to the Colorado Springs Fire Department - Development Review Enterprise - at 2880 International Circle - Suite 200-7.|
|FYI||(STANDARD COMMENT) REVIEWS:
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirement are met as established by the Authority Having Jurisdiction, whether of not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the fire code requirements of the adopted International Fire Code, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.