NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
02153 VICTOR PL
||FYI||6/30/14 RESUBMITTED WITH LETTER FROM ARCHITECT AND STAMPED
ONE @ 100 gallons
Installation per IFC 2009, chapter 38, AND NFPA 58.
less than 100 gallons is below LPG permit amount @ 125 gals w.c.|
||FYI||This project is:Unknown Tenant 2155 Victor Pl Change of Occupancy
SYSTEMS: NO SYSTEMS IN THIS BUILDING
CN:Code: 09 IBC - 09 IFC - 11 PPRBC /Class: B/F-2 / Const: V-B /Stories: 1 /Size: 4200 /OL: 23
FH:Required Flow: gpm /# Hydrants /On site flow:
|Disapproved||CHEMICAL INVENTORY, AS DECLARED
SEE ELECTRONIC DOCUMENTS:
Owner Statement: "No chemicals materials and no extractions will be done in the greenhouse."
(plans as submitted) Owner's declaration: that LPG will be stored or used on site,however, no amounts, locations, number of cylinders or purpose for the LPG was identified. This information is needed in order to complete a plan review.
A letter was delivered to CSFD on 6/19/14 (p.m.) and dated 6/19/14 by B&H Engineers, Mr. Parsay. SEE ELECTRONIC DOCUMENTS. Letter states "Propane tanks for heating greenhouse are not exceeding 100 gallons each." No further information was provided.
Please provide the following information:
How many cylinders?
Total number of cylinders and specific quantities of each cylinder?
LPG report amounts in water gallon capacity
What type of heaters? are these permanent? Submit specifications on units.
Devices and equipment shall be approved for use (listed and labeled) with LP gas.
Where are the heating units located?
LP gas equipment shall be installed in accordance with the International Fuel Gas Code and NFPA 58, except otherwise provided in Chapter 38 of the IFC 2009.
LP GAS CHAPTER 38 OF IFC 2009
NFPA 58 current edition