NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
ART C KLEIN CONSTRUCTION CORPORATE OFFICE
03370 CHELTON LP
||FYI||*****(STANDARD COMMENT 1) This project is: Art Klein 3370 Chelton Lp S Deficiency correction
This plan review is based on the requirements found within the adopted Editions of the International Building Code, International Fire Code and the related Standards.|
|FYI||***** 20-HEAD LETTER:
Date Submitted: 12/27/13
Total number of heads affected : 16 plus floater main
Location of work: Warehouse where halon system previously existed
Bldg permit #: N/A
Flex Connections approved in this facility?: NO
Brand: if known
Equivalent Length: if known
UL 2443/FM 1637 Complaint:|
||Disapproved||*****20-HEAD LETTER DISAPPROVALS
-----Multiple letters have been submitted for this scope of work/building permit, thus the total modifications exceed 20-heads.
--XX---The information you have provided is not complete, please provide the following:
Why is work being completed if there is no construction. This is quite a few
heads to be for "Sprinkler Work Only"
--XX---It appears a building permit is required for the construction work associated with this work.