NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
04110 BRIARGATE PKWY
||FYI||*****(STANDARD COMMENT) This project is: Memorial MOB 4110 Briargate Py 105 New MRI Suite
Date of Plans: 10/10/13
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.
|FYI||SEE ELECTRONIC DOCUMENTS
LETTER DATED NOV 18 2013 describes hazardous materials and design for MRI:
Inert Cryogen helium for MRI @ 1,731 L = 45,748 CF @ 70 deg F @ 1 atm
R-22 refrigerant for MRI chiller @ 45 lb + 15 lb + 7.2 lb
refrigerant monitor, EM power, EPO switch purge exhaust = refrigerant room design. OK
MRI CHILLER uses propylene glycol cooling @ 30% 200 gallons
This facility is required to complete a Hazardous Materials Construction final inspection. Please contact 719-385-5978 to schedule your inspections; Hazmat Specialist, Jay Weightman,
This facility is enrolled in the Hazardous Materials Annual Permit Program. Please update the MRI materials into the data base at https://hammers.springsgov.com/submit
|Attention||Equipment, machinery, and required detection and alarm systems associated with the use, storage, or handling of hazardous materials shall be listed or approved. This requirement is subject to verification at the time of the Hazardous materials Inspection prior to signing the Fire Final.
** Please be prepared to demonstrate the refrigerant and any additional monitoring and alarm systems at the time of inspection|