NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
GREAT WESTERN BANK
05225 ACADEMY BLVD
||FYI||*****(STANDARD COMMENT 1) This project is: Plumtree Office Building, 5225 N Academy Blvd: fire alarm panel replacement
This plan review is based on the requirements found within the adopted Editions of the International Building Code, International Fire Code and the related Standards.|
|FYI||(STANDARD COMMENT) REVIEWS:
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirement are met as established by the Authority Having Jurisdiction, whether of not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the fire code requirements of the adopted International Fire Code, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.
|Disapproved||*****(STANDARD COMMENT 19) DISAPPROVED COMMENTS
The following information and/or corrections are needed prior to completing a full plan review. Please respond, in writing on letterhead, to each of the following comments:
1. This appears to be the start of a system-wide replacement/upgrade. CSFD will require a meeting with permit applicants and building owner or representative to discuss this work.
2. building key plan was not provided as required.
A complete review was NOT conducted until we determine what the final scope will be.
Also review the disapproved plans for additional written comments prior to submittal of new plans.
|FYI||(STANDARD COMMENT 20) CORRECTIONS
All corrections and comments are to be submitted back to CSFD in writing, or provid submittal sheets/drawings, etc as requested, to complete the review. Corrections are not accepted over the phone, via fax, email or verbally.|
|Attention||(STANDARD COMMENT 26) THE DISAPPROVED ITEMS MAY NOT CONSITITUE A COMPLETE LIST OF VIOLATIONS.
It is the responsibility of the design professional to conduct a complete re-review of the plans for additional violations of the adopted codes/standards and incorrect information prior to resubmitting.|
|FYI||(STANDARD COMMENT) DEW REVIEWER CONTACT:
If you have any specific questions or concerns about these comments, please feel free to contact me at:
Doreen "Dee" Withee, CFPS
Fire Protection Engineer II, CSFD
2880 International Circle, Suite 200-7
Colorado Springs, CO 80910
(T) 719-385-7361 / (F) 719-385-7330