NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
SDS FINISHED WATER PUMP STATION AREA 80
00977 MARKSHEFFEL RD
||FYI|| The material categories identified in this facility are classified as physical and health hazards.
Flammable liquids and
Oxidizer, solids or liquids.
Water-reactive materials solids or liquids.
Highly Toxic & Toxic materials.
Narrative review and plan sheets show designs were based on code compliance within the IFC code chapters respectively.
Material labeling, placards and all hazards shall be labeled in accordance withe the requirements of the IFC 2009 and NFPA 704, ASME B.31 for industrial processes and piping as applicable.|
|FYI||Phone call with V Hart & Chris, Carollo
Re: gas detection, monitoring, alarm, systems on generator EM and standby; instrumentation, processes.
Flooring is vinyl ester compatible with all materials in use & storage>
All process and hazardous materials areas are on monitoring and alarm systems for leaks: on back up UPS and to generator.
Per V Hart Tanks will be permitted through CSU at deferred separate cover.
Addiitional plan sheets emailed showing LOX tank drawings, the containment detection, the chlorine detection, and the ozone/oxygen monitors.|
||E-Mail||06/27/13 Plan Reviewer contacted design firm Mr. Hart for Hazmat Plans and to isolate areas out of plan sheets. Mr. Hart requested plan reviewer hold on to plans until hazmat plan sheets sent to HM reviewer for review. Mr. Hart to send Hazmat related design documents via email. OK per Plan reviewer
06/28/13: received plan sheets via email p.m.
highlighted areas not reflected on pdf format. Will speak with Mr. Hart 7/1/13.
|FYI||*****(STANDARD COMMENT) This project is: Southern Delivery System Water Treatment Plant, 977 N Marksheffel Rd: Finished Water Pump Station Area 80
Date of Plans: 5.29.13
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.|