||FYI||*****(STANDARD COMMENT) This project is: Mike Shaw Pre Owned Car Sales Office. 1237 Motor City Dr: new sales building
Date of Plans: 9.25.13
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.
|FYI||*****(STANDARD COMMENT) HYDRANT REQUIREMENTS:
Size of Bldg. 4814-- sq ft
Construction Type -II-B-
Fire Sprinklers Y-- N-XXX-
Fire Walls being installed Y -- N XXX--;
Required GPM: -1500- gpm
# of hydrant(s) required: 1--
Max AVG spacing between hydrants: 500-- ft
Max hose lay: 250ft
|Disapproved||*****(STANDARD COMMENT 19) DISAPPROVED COMMENTS
The following information and/or corrections are needed prior to completing a full plan review. Please respond, in writing on letterhead, to each of the following comments:
1. All new structures shall have adequate fire flow water supplies. Only 1 hydrant is shown and it is unknown if that hydrant has adequate fire flow.
Also review the disapproved plans for additional written comments prior to submittal of new plans.|
|Disapproved||(STANDARD COMMENT) WATER PLANS
The City APPROVED" utility service plans are to be ATTACHED to all sets of construction plans for CSFD plan reviews.
|Disapproved||(DISAPPROVED) FIRE FLOW REPORT
Provide confirmation on the fire flow results from Colorado Springs Utilities. A copy of their report for this area is required to be provided with your plan submittals.
When multiple fire flows are provided from CSU, please indicate all flows on your submitted plans.
NOTE - To request a fire flow report, please go to: https://www.csu.org/Pages/construction-drawing-review.aspx
|FYI||(STANDARD COMMENT) CORRECTIONS
All corrections and comments are to be submitted back to CSFD in writing, or provid submittal sheets/drawings, etc as requested, to complete the review. Corrections are not accepted over the phone, via fax or verbally.
|FYI||(STANDARD COMMENT) RESUBMITTALS
Re-reviews may be submitted back to the CSFD by direct submittal at the Construction Services counter, or through the Regional Building Department's routing system.
|FYI||(STANDARD COMMENT) REVIEWS
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirements are met as established by the Authority Having Jurisdiction, whether or not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the adopted fire code requirements, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.