||FYI||*****(STANDARD COMMENT) This project is: Canyon Reserve Townhomes, 5967 Canyon Reserve Hts
Date of Plans: 5.13.13
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.
|Attention||*****(STANDARD COMMENT) RED-LINED COMMENTS
The following RED-LINED items are to be corrected prior to final inspection:
1. Plans appear to comply with ignition resistant construction for new construction as per development plan - ensure the following: a) Stucco is sealed at the bottom with exception of the occasional weep holes no larger than 1/8-inch.
b) Fuels Management is adhered to.
c) Class A Roofing is utilized - reference redlines sheet A0.1
|Attention||(STANDARD COMMENT) CONSTRUCTION SPLICES
You are strongly encouraged to have any splices that may occur during this project, reviewed by CSFD. Failure to do so, can result in coordination issues that could prevent a final inspection from being completed, thus delaying the issuance of a Certificate of Occupancy.
|FYI||(STANDARD COMMENT) WATER SUPPLY REQUIRED ON SITE
Required water supplies for fire protection, either temporary or permanent, shall be made available as soon as combustible material arrives on the site. (2009 1412)|
|FYI||(STANDARD COMMENT) FIRE FLOW TEST RESULTS REQUIRED - EXISTING HYDRANTS:
Actual hydrant flow test results dated within 5 years shall be provided prior to the arrival of combustible material on the construction site.|
|FYI||(STANDARD COMMENT) CONTACTS FOR FLOW TESTING HYDRANTS
PUBLIC/CITY OWNED HYDRANTS: Contact SEAN HIGBEE, CSU at 668-4595 or via email at email@example.com to schedule an ACTUAL flow test. Be sure to provide them with a CSFD plan review number to include with their flow reports. CSFD need not be present when City Utilities flow tests hydrants as we will accept their reports. PLEASE ALLOW 1-2 WEEKS NOTICE
PRIVATE HYDRANTS: Contact your assigned inspector to schedule a flow test of PRIVATE OWNED hydrants. A contractor capable of performing the test will be required as CSFD Inspectors WITNESS only. CSFD will not accept flow test results we have not witnessed.|
|FYI||(STANDARD COMMENT) FIRE EXTINGUISHERS - MULTI-FAMILY RESIDENTIAL OCCUPANCIES
OPTION #1 -- Install 2A-10B:C fire extinguishers at a rate of 1 unit per 3000 squre feet, AND a maximum of 75-ft travel distance. These extinguishers are to be located in the common areas of the complex. History shows they are often stolen, therefore option 2 is highly recommend.
OPTION #2 -- Install (1) 1A-10B:C ext. in each apartment/town home. It's ok to hang under a kitchen sink, in a closet, or in an ATTACHED garage, just remember to make sure it's accessible
Install extinguishers in highly visible and accessible locations, never in a dead-end area, and always try to place them near an exit pathway or at an exit(s). Mount 4" off floor to a maximum of 5 ft. to the top of the fire ext. (HINT: About waist high is perfect.) "FIRE EXTINGUISHER" signs may need to be posted too properly identify where the units are located if they're not highly visible.
|FYI||(STANDARD COMMENT) ADDRESSING
Address shall be posted on street addressed side of structure. Minimum 5" numbers with 1/2" stroke. Contrasting color to background. (2009 IFC 505.1)|
|FYI||(STANDARD COMMENT 10) INSPECTIONS
Due to the dynamic nature of inspectors schedules, PLEASE call your inspection requests in with ample time to allow scheduling.
When calling, please have your complete CSFD plan review number(s) ready for each inspection request.
( i.e. 20001234 - HM -2 or 20000012 - CN - 1)
The CSFD Approved sets of plans are to be on site for all inspections.|
|FYI||(STANDARD COMMENT) SCHEDULING INSPECTIONS:
Please call 719-385-5982 Extension 2 to schedule all construction related inspection activities.|
|FYI||(STANDARD COMMENT) REVIEWS
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirements are met as established by the Authority Having Jurisdiction, whether or not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the adopted fire code requirements, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.
|FYI||(STANDARD COMMENT) PERMITS
Insure all applicable permits are obtained from the Regional Building Department and the Colorado Springs Fire Department for the work that is being done at this site.