NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
ELLICOTT MIDDLE SCHOOL
00350 ELLICOTT HY
||FYI||RESUBMITTED: The plans have been re-submitted, and the disapproved issues have been addressed as follows: APPROVED
**PLEASE NOTE** ALL COMMENTS FOUND ON PREVIOUS PLAN REVIEWS REMAIN ENFORCEABLE UNLESS OTHERWISE NOTED IN THIS REVIEW.
1) Narrative letter dated May 2, 2013 from Ellicott Middle School describing materials, inventory and activities at this school. Minimal amount of food grade chemistry. SEE ELECTRONIC DOCUMENTS.
No further review.
2) LPGAS tank installation permit is required to be submitted under separate cover and deferred to later period; Henderson LP vendor.|
||FYI||This project is:
Ellicott Middle School, 350 Ellicott Hy: new middle school
SYSTEMS: fire sprinkler for occupancy; fire alarm for occupancy; kitchen suppression
CN:Code: 06 IBC - 06 IFC - n/a PPRBC /Class: E, B/ Const: II-B /Stories: 2/Size: 51,564 /OL: 1453
Additional Comments: No site or water reviews on this project; project reviewed at request of EFPD
ATTENTION: See our web site for our latest plan review comments for your job at:
www.springsgov.com - go to "City Agencies" (tab on the teal bar to get a drop box) - click on - "Fire Department" - (Using the links down the left side of the page), click on - "Web Guide." Once you're into the Web Guide, click on "Plan Review Status" This will also give you access to numerous other items that may assist you in your future project design work.
|Disapproved||The following information and/or corrections are needed prior to completing a full plan review. Please respond, in writing, to each of the following comments:
THE CHEMICAL INVENTORY, AS DECLARED
Not provided with this plan set
Per phone conversation with Mr. Kimes 4/24/13
No industrial arts
No lawn maintenance equip or fuels
Outside janitorial service to be provided; minimal janitorial supplies
Food grade chemistry
No chemistry/biology lab storage or labs
Kiln has been reviewed by PPRBD Mechanical Dept.
*** Mr. Kimes shall resubmit plans with an attached chemical inventory of proposed school and narrative statement describing above materials and/or activities. Minimus amounts of material may be located at this facility. Below IFC 2009, hazardous materials permit threshold amounts.
|Attention|| A permit is required to store, use, handle, or dispense LP-gas or to install or maintain any LP-gas container of 125-gallon or greater aggregate water capacity. Please contact CSFD Office of the Fire Marshal at (719) 385-5978 to obtain the proper forms or additional information.
**** The installation, transportation, storage, and maintenance of LP-gas and associated equipment shall be performed in accordance with the International Fire Code and applicable referenced standards (NFPA 58 current edition).
LP gas tank is proposed to be installed underground to supply fuel for the generator on site.
PLAN SHEET SD1.1 note #39
Henderson is the proposed vendor and shall be required to apply for the LP GAS STORAGE TANK INSTALLATION PERMIT UNDER SEPARATE COVER AND DEFERRED SUBMITTAL.