||Approved||Originally processed as plans and permit. DFM Cooper allowed this to be a residential fee, however permit and inspection is required.|
||FYI||*****(STANDARD COMMENT 1) This project is: Beth Lee House, 1929 Meyers: add/relocate fire sprinklers at owner request
Date of Plans: 2.11.13
|FYI||(STANDARD COMMENT 3) HEAD EXTENDERS:
BE ADVISED: Head Extenders are not allowed in the City of Colorado Springs effective Immediately. 1/08|
|FYI||*****(STANDARD COMMENT 6) The fire sprinkler system is being installed by: WSFP
This plan review is based on the requirements found within the adopted International Building Code, International Fire Code, and the 2010 editions of NFPA Standard 13, 13R or 13D as applicable.
CSFD does not allow any combustibles into a building until a sprinkler system has passed it's final acceptance test performed by CSFD Inspector's.|
|FYI||*****(STANDARD COMMENT 8) SCOPE OF WORK:
Area/scope of work is ---3-- SPRINKLERS IN SITTING AREA-------of the building.
Flex Connections: NOT PERMITTED
|FYI||*****(STANDARD COMMENT 10) WATER SUPPLY/SYSTEM DEMAND INFORMATION:
The Water Flow Calculation show a water supply of having a 48- PSI Static; 44 PSI Residual; 30- GPM Flow.
System Demand of 28 - gpm at 33- psi is needed at the TANK
All hydraulic designed systems are to have the Hydraulic Placard information sign secured to the sprinkler riser.|
|FYI||(13-D) BUCKET TEST:
All 13-D systems will require a bucket test. |
|FYI||(13-D) TEMPERATURE RATING:
Sprinklers shall be installed in accorance with NFPA 13D Table 18.104.22.168 when installing near specific heat sources.|
|FYI||(13-D) CEILING FANS/LIGHT FIXTURES:
Pendent sprinklers shall be located at least 3-ft from obstructions such as ceiling fans and light fixtures.
Sidewall sprinklers shall be located at least 5-ft from obstructions such as ceiling fans and light fixtures.
Where the area of the fan blades encompasses more than 50% of the area of the plan view, additional sprinklers may be required.
(NFPA 13D:22.214.171.124 and 126.96.36.199)|
|FYI||(STANDARD COMMENT 20) LICENSED INSTALLER:
An On-Site Installer shall supervise all on-site work on any fire sprinkler project. This On-Site Installer shall have a current Installer Card issued by RBD, on his person, while on the job site.
|FYI||(STANDARD COMMENT 23) MANUFACTURER'S SPECIFICATIONS:
The approved set of Fire Sprinkler Plans, cut sheets on all equipment being installed, and the installation permit are to be on site for all fire department inspections.|
|FYI||(STANDARD COMMENT 24) CPVC PIPING:
Exposed CPVC piping shall be installed per manufacturer's specifications.
Never test the system integrity using air or compressed gas!
Compatibility with other building components including insulation, fire caulking, plastic sheeting, and other petroleum based products, shall be verified prior to use with CPVC.
Insure the pipe is installed in locations that will help prevent damage caused by physical contact.
|FYI||(STANDARD COMMENT) CPVC ROUGH INSPECTIONS:
Effectively Immediately: Sprinkler Heads shall not be installed on CPVC piping until CSFD has witnessed a visual rough-inspection of all piping and granted permission to install sprinklers.|
|FYI||(STANDARD COMMENT 26) CONCEALED SPACES -
This plan did not provide any information on combustible concealed spaces. NFPA 13 requires that "All concealed spaces enclosed wholly or partially by exposed combustible construction shall be protected by sprinklers". There are 12 specific allowances to this section that allow for the omission of sprinklers. If there are combustible concealed areas found during the installation of the system that do not meet the requirements of the 12 allowances, then these areas will be required to be sprinkled. (NFPA 13:8.15.1)
IT IS THE RESPONSIBILITY OF THE INSTALLER TO MAKE SURE THAT THE SYSTEM IS INSTALLED IN ACCORDANCE WITH THE STANDARD.|
|FYI||(STANDARD COMMENT 27) FREEZING CONDITIONS
It is the designer's responsibility to provide the building owner with a system design that will continue to function reliably even under adverse temperature conditions. The sprinkler contractor must be conscious of field conditions that may affect the performance of their system, such as drafts, disturbed insulation, installation along exterior walls, etc. and incorporate such conditions into a reliable design.|
|FYI||(STANDARD COMMENT 35) CERTIFICATE OF INSTALLATION:
It is the installer's responsibility to certify through this form (attached to the plans) that the system has been properly installed and tested.
The form is to be filled out in its entirety PRIOR TO THE ARRIVAL OF THE FIRE INSPECTOR conducting the final inspection and/or acceptance test of the system.
FINAL INSPECTIONS WILL NOT BE CONDUCTED WITHOUT THIS FORM BEING COMPLETED.
|FYI||(STANDARD COMMENT 36) GENERAL INFORMATION SIGN
A general information sign used to identify the system design basis and information relative to the requirements of NFPA 25, shall be provided with a permanently marked weather-proof metal or rigid plastic sign, secured at each system control riser, antifreeze loop and auxiliary control valve.
|FYI||(STANDARD COMMENT 10) INSPECTIONS
Due to the dynamic nature of inspectors schedules, PLEASE call your inspection requests in with ample time to allow scheduling.
When calling, please have your complete CSFD plan review number(s) ready for each inspection request.
( i.e. 20001234 - HM -2 or 20000012 - CN - 1)
The CSFD Approved sets of plans are to be on site for all inspections.|
|Attention||(STANDARD COMMENT) JAH - SCHEUDLING INSPECTIONS:
Your assigned inspector is Jeff Hanenberg. Please call 719-385-5982 and choose option 2 to schedule all construction related inspection activities.
|FYI||(STANDARD COMMENT 37) ROUGH VISUAL INSPECTIONS:
Rough Visual inspections shall be completed PRIOR TO any bucket tests or final inspections.|
|FYI||(STANDARD COMMENT 38) CONCEALED WORK:
The fire sprinkler piping shall not be covered up by walls, sheetrock, ceiling tiles, etc... prior to the CSFD visual inspections of the piping. If the piping is covered, and the inspectors cannot inspect it as is required by Fire Code, the walls,sheetrock, ceiling tiles, etc... will be required to be removed. If this means that finished ceilings will need to be removed, this will be required to be done!
|FYI||(STANDARD COMMENT 39) PLAN REVIEW/PERMIT FEES:
All fire department fees are to be paid prior to issuance of any permits. These fees must be paid directly to the Colorado Springs Fire Department - Development Review Enterprise - at 2880 International Circle - Suite 200-7. |
|FYI||(STANDARD COMMENT) REVIEWS:
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirement are met as established by the Authority Having Jurisdiction, whether of not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the fire code requirements of the 2003 International Fire Code, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.