Per Chad (GC or Art Klein) Unknown
No chemicals or hazardous materials are a part of the scope of this project nor will there be any impact to any potential existing materials.
Installation of security screening equipment only.
Per HM plan reviewer:
Radiioactive sealed sources are regulated through the NRC and EPA, and permitted through the CDPHE. These materials on no longer managed through the IFC.
The TSA may report these during their annual hazardous materials inspection to the Hazmat Inspector. These materials may also (recommmended) be reported in the CSFD's online webbased reporting system to be activated in 2013.
NO HAZMAT CONSTRUCTION INSPECTION REQUIRED.
THE HAZARDOUS MATERIALS PERMIT INSPECTION/INPSECTOR SHALL FOLLOW UP WITH THE TSA FOR THIS INFORMATION.
HAZMAT REVIEW = N/A
||FYI||*****(STANDARD COMMENT) This project is: Colorado Springs Airport, 7770 Milton E Proby: interior remodel - security screening - new scan equipment
Date of Plans: 2.7.13
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.
|FYI||(STANDARD COMMENT) IMPACT TO EXITING AND/OR FIRE PROTECTION SYSTEMS
Egress components and fire protection systems that may be negatively impacted by yoru scope of work will be required to comply with the currently adopted fire code. As an example, if your work increases the occupant load of a space, the existing egress components will be required to comply with the requirements of the new occupant load.|
|Attention||(STANDARD COMMENT) CONSTRUCTION SPLICES
You are strongly encouraged to have any splices that may occur during this project, reviewed by CSFD. Failure to do so, can result in coordination issues that could prevent a final inspection from being completed, thus delaying the issuance of a Certificate of Occupancy.
|FYI||(STANDARD COMMENT) HAZ-MAT REVIEW REQUIRED
It appears that hazardous materials may be located on site. Your plans have been forwarded to the HazMat reviewer.
If hazardous materials exceed exempt amounts, you will also be required to submit a Hazardous Material Management Plan for annual permitting.
Additional tank installation permits and plan reviews may also be required. Check with the CSFD for details.
|FYI||*****(STANDARD COMMENT) FIRE PROTECTION SYSTEMS
The following systems are present or required in this facility:
---XXX--Fire Alarm System
-XXX----Water-Based Suppression System (fire sprinklers, standpipes, etc)
Applicable Fire Protection System plans shall be submitted to the CSFD Construction Services office in the Regional Development Center.
|FYI||(STANDARD COMMENT 10) INSPECTIONS
Due to the dynamic nature of inspectors schedules, PLEASE call your inspection requests in with ample time to allow scheduling.
When calling, please have your complete CSFD plan review number(s) ready for each inspection request.
( i.e. 20001234 - HM -2 or 20000012 - CN - 1)
The CSFD Approved sets of plans are to be on site for all inspections.|
|FYI||(STANDARD COMMENT) JAH - SCHEDULING INSPECTIONS:
Your assigned inspector is Jeff Hanenberg. Please call 719-385-5982 Extension 2 to schedule all construction related inspection activities.
|FYI||(STANDARD COMMENT) REVIEWS
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirements are met as established by the Authority Having Jurisdiction, whether or not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the adopted fire code requirements, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.
|FYI||(STANDARD COMMENT) PERMITS
Insure all applicable permits are obtained from the Regional Building Department and the Colorado Springs Fire Department for the work that is being done at this site.