NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
CITY OF CS AIRPORT MAIN
07770 MILTON E PROBY PY
||FYI||***** 5-DEVICE LETTER:
Date Submitted: 02/18/13
Date of Work: 02/20/13
Contractor: Foster Electric
Scope : Adding relocating notification, adding smoke detector
Current Draw: 20.666
Battery Size: 12V/33AH
Location of work: Screening area and IT Rm 202
Bldg permit #: I62217
||Disapproved||***** 5-DEVICE LETTER DISAPPROVALS:
-----Multiple letters have been submitted for this scope of work/building permit, thus the total modifications exceed 5 devices.
-----Your company is currently restricted from use of this privilege through a ruling from Fire Board of Appeals.
-----Your company is currently not licensed to perform work on fire suppression systems, please contact Contractor Licensing at 719-327-2880 to correct this.
-----The information you have provided is not correct:
It appears this letter has the incorrect CSFD Plan Review number and RBD Permit #.
|Disapproved||The plan review number and permit you cited on this letter show that there is already a permit for alarms#.
I did a search for plan reviews and RBD permits and it appears you may have intended this to be attached to CSFD Plan Review 2013-0112 and RBD Permit I62217.
Please verify through the general contractor (back signature sticker on his plans) and confirm to me so I can process this letter.
Colorado Springs Fire Department
2880 International Circle, Suite 200-7
Colorado Springs, CO 80910
Providing the highest quality problem solving and emergency services to our community since 1894