||FYI||*****(STANDARD COMMENT 1) This project is: Carmax 4010 Tutt Bd Change in monitoring and dialer
Date of Plans: 01/03/12
You can access our web site for the latest fire department plan review comments:
1. From www.springsgov.com, select CITY AGENCIES then FIRE
2. Click on FIRE CODE ENFORCEMENT.
3. Click on REVIEW PLANS STATUS in the gray box
4. Then select VIEW PLAN REVIEW STATUS.
5. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.|
|FYI||*****(STANDARD COMMENT 5) DESIGNER/INSTALLER INFORMATION
Fire Alarm system was designed by: Cintas
Fire alarm system is being installed by: Cintas
This plan review is based on the requirements found within the adopted Editions of the International Building Code, International Fire Code and the related Standards.|
|FYI||(STANDARD COMMENT) ADDITIONS AND REMODELS TO EXISTING SYSTEMS:
Existing systems shall comply with current codes and standards for all areas occupied by the tenant, not just the area of remodel.
(CSFD Administrative Ruling 2010-2)|
|FYI||*****(STANDARD COMMENT 7) Scope of Work: Adding new dialer and monitoring. Re-programming of existing panel dialer will void warranty on panel.
EXISTING CONDITIONS AS DECLARED:
Manual, automatic, sprinkler monitoring; DACT; B Class; 0 Survivability|
|FYI||(COMMERCIAL) CONTROL PANEL SMOKE DETECTION
A smoke detector is to be installed at the location of each fire alarm control unit, notification appliance circuit power extenders (NAC/Power Supply Panels) and supervising station transmitting equipment. This detector is to be installed in an area and manner that is in accordance with it listing. (NFPA 72:10.15)
Off-site monitoring of this fire alarm system is required and shall be provided by an approved monitoring agency.
The phone number to be used to report a fire emergency is (719) 444-7632.
Refer to the NFPA Standard 72, Chapter 26 for information of how this requirement may be met.
Two separate phone lines may be needed to meet this requirement.
NOTE - The monitoring of the fire alarm system is dependent on the proper operation of the communicator panel and notification of the building occupants of any malfunctions.
|FYI||(COMMERCIAL) MONITORING FOR INTEGRITY:
All means of interconnecting equipment, devices, appliances and wiring connections shall be monitored for the integrity of interconnecting conductors or equivalent path.
Monitoring for integrity shall not be required for the interconnection between enclosures containing control equipment located within 20-feet of each other where the conductors are installed in conduit or equivalently protected against mechanical injury.
This includes all panels, sub-panels, communications methods, notification appliances, initiating devices, etc.
|FYI||(COMMERCIAL) DACT COMMUNICATIONS
The DACT shall be connected to the public switched telephone network ahead of any privately owned equipment (22.214.171.124.1)
The primary communication method shall be a POTS loop-start telephone line. The required secondary communication method may be as permitted by 126.96.36.199.1.4(A).|
|FYI||(STANDARD COMMENT 13) LICENSED INSTALLER/SERVICE TECHNICIAN
An On-Site Installer/Service Technicial shall supervise all on-site work on any fire protection system. This On-Site Installer shall have a current Installer Certificate (RBD Wallet Card), on his/her person, while on the job site.|
|FYI||(STANDARD COMMENT 9) CERTIFICATE OF INSTALLATION
It is the installers responsibility to certify, through the use of this form, that the system has been properly installed and tested.
The form is to be filled out in its entirety PRIOR TO THE ARRIVAL OF THE FIRE INSPECTOR conducting the final inspection and/or the acceptance test of the system.
FINAL INSPECTIONS WILL NOT BE CONDUCTED WITHOUT THIS FORM BEING COMPLETED.
At the time of this inspection the Fire Inspector will expect ALL devices involved in this fire alarm project to be tested. The installer should be aware of the fact that in a larger facility there may by a need to isolate the fire alarm system to only the area being tested. This testing method may be needed in such buildings as Hospitals, High Rise office buildings, and Malls to name a few. Regardless of how the fire alarm test is going to be conducted the alarm installer is to insure that building owner and/or manager and the General Contractor has been informed of the test criteria, time and date of the test, and have given their approval.
NOTE - Fire alarm installers shall also complete the "RECORD OF COMPLETION" forms prior to scheduling a fire alarm final. A copy of this form can be found in NFPA 72.|
|FYI||(STANDARD COMMENT) RECORD OF COMPLETION:
The Record of Completion (ROC) shall be filled out in accordance with 10.18.2 for new installations.
All modifications made after the initial installation shall be recorded on a revised Record of Completion. All changes shall be shown and the revised ROC and shall include a revision date.
|FYI||(STANDARD COMMENT) PRE-TEST REQUIREMENT:
Before requesting final approval of the installation, the installing contractor shall furnish a written statement that the system has been installed in accordance with approved plans and testing in accordance with the manufacturer's published instructions and the appropriate NFPA requirements. (10.18.1.3)
CSFD requires a 100% pre-test - Evidence may be documented on the Record of Completion.|
|FYI||(STANDARD COMMENT) 100% ACCEPTANCE TESTING
At the time of this inspection the Fire Inspector will expect ALL devices involved in this fire alarm project to be tested. The installer should be aware of the fact that in a larger facility there may by a need to isolate the fire alarm system to only the area being tested. This testing method may be needed in such buildings as Hospitals, High Rise office buildings, and Malls to name a few. Regardless of how the fire alarm test is going to be conducted the alarm installer is to insure that building owner and/or manager and the General Contractor has been informed of the test criteria, time and date of the test, and have given their approval. |
|Attention||(STANDARD COMMENT 11) ROUGH-IN PERMIT AND INSPECTIONS:
All Fire Alarm systems wiring installed within the City of Colorado Springs must be inspected by the Pikes Peak Regional Building Department PRIOR TO the Fire Final on the system. This will require the installing contractor to obtain a Rough-In Permit issued by the Regional Building Department. Please call RBD at 327-2880 for additional information on how to obtain this permit.|
|FYI||(STANDARD COMMENT 14) MANUFACTURER'S SPECIFICATIONS
The approved set of plans, manufacture's product data sheets on all equipment being installed, and the installation permit are to be on site for all fire department inspections.|
|FYI||(STANDARD COMMENT 10) INSPECTIONS
Due to the dynamic nature of inspectors schedules, PLEASE call your inspection requests in with ample time to allow scheduling.
When calling, please have your complete CSFD plan review number(s) ready for each inspection request.
( i.e. 20001234 - HM -2 or 20000012 - CN - 1)
The CSFD Approved sets of plans are to be on site for all inspections.
CALL 719-385-5982 AND CHOOSE OPTION 2 TO SCHEDULE INSPECTIONS.|
|FYI||(STANDARD COMMENT 19) PLAN REVIEW/PERMIT FEES
All fire department fees are to be paid prior to issuance of any permits. These fees must be paid directly to the Colorado Springs Fire Department - Development Review Enterprise - at 2880 International Circle - Suite 200-7.|
|FYI||(STANDARD COMMENT) REVIEWS:
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirement are met as established by the Authority Having Jurisdiction, whether of not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the fire code requirements of the 2003 International Fire Code, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.