||FYI||*****(STANDARD COMMENT 1) This project is: Villages at Wolf Ranch Filing 20. Located northeast of Wolf Center Drive and Research Parkway.
Date of Plans: 3.19.13
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.|
|Attention||*****(STANDARD COMMENT 2) BUILDING DATA:
Size of Bldg. --7700--- sq ft MAXIMUM
Construction Type --V-B----
Fire Sprinklers Y----- N--XXX---
Fire Walls Y ----- N ---XXX--
Required GPM: ---2250-- gpm
# of hydrant(s) required: --2---
Max AVG spacing between hydrants: -450---- ft
Max hose lay: ---225-- ft
|FYI||*****(STANDARD COMMENT) SCOPE OF WORK:
-----WATER PLAN - SINGLE FAMILY SUBDIVISION - NO FIRE INSPECTION|
|Attention||(STANDARD COMMENT) READY FOR SIGNATURES:
The water plans appear ready for signature as long as all disapproved comments have been addressed. Please provide one hard copy for CSFD records along with your final copies for our signature.
|FYI||(STANDARD COMMENT 6) This is a PUBLIC water system.|
|FYI||(STANDARD COMMENT) REVIEWS:
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirement are met as established by the Authority Having Jurisdiction, whether of not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the fire code requirements of the 2003 International Fire Code, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.