NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
RAMPART SUPPLY INC
01801 UNION BL
||FYI||*****(STANDARD COMMENT 1) This project is: Rampart Supply, 1801 S Union: fire line replacement
Date of Plans: 11.7.12
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.|
|FYI||*****(STANDARD COMMENT) SCOPE OF WORK:
----XXX-UTILITY SERVICE PLAN
|Attention||FLUSH AND HYDROSTATIC TESTING:
All piping and attached appurtenances subjected to system working pressure shall be hydrostatically tested at 200 psi or 50 psi in excess of the system working pressure, which ever is greater, and shall maintain that pressure +/- 5 psi for 2 hours. (NFPA 13:10.10.2.2)
The Flush and Hydrostatic test of fire service mains and lead-in piping to system risers is to be completed and approved prior to connecting the riser to the underground mains and/or lead-ins. The flushing and pressure test is to be witnessed and approved in writing by a member of the Colorado Springs Fire Dept. |
|FYI||(STANDARD COMMENT 8) GENERAL INSPECTIONS/PLANS & SCHEDULING
Minimum notice of one week is required for all inspections. PLEASE plan ahead - call your inspections in with ample time to allow adequate scheduling.
When calling, please have your complete CSFD plan review number(s) ready for each inspection request.
( For Example: 2005-1234- HS-2)
The CSFD APPROVED sets of plans SHALL be on site for all inspections.
|FYI||(STANDARD COMMENT 11) JAH - SCHEDULING INSPECTIONS:
Your assigned Inspector is Jeff Hanenberg. Please call 719-385-5982 Extension 2 to schedule all construction related inspection activities.|
|FYI||(STANDARD COMMENT) REVIEWS:
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirement are met as established by the Authority Having Jurisdiction, whether of not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the fire code requirements of the 2003 International Fire Code, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.