NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
01855 TELSTAR DR
||FYI||USAA, 1855 Telstar: interior remodel - UPS and mechanical systems, battery back up and generator room
SYSTEMS: fire sprinkler for area; fire alarm for occupancy
CN:Code: 09 IBC - 09 IFC - 11 PPRBC /Class: B/ Const: I-A /Stories:5 /Size: 9770 THIS SCOPE /OL: NO CHANGE
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.|
|Attention||BATTERIES SYSTEMS SHALL BE IN ACCORDANCE WITH SECTION 608 OF THE IFC 2009:
1. The batteries shall have venting caps to relieve pressure, which is often Hydrogen gas.
2. VRLA or other sealed non-venting caps shall be equipped with resealing flame arresting safety caps.
3. Lithium Ion and Lithium metal polymer batteries shall not require vented caps.
4. VRLA and Lithium -ion and lithium metal polymer battery systems shall be provided with a listed device or other approved method to preclude, detect or control Thermal runaway.
5. Battery systems shall be permitted in the same room or area as they equipment they support.
6. Battery systems shall be housed in a non-combustible locked cabinet or enclosure to prevent unauthorized personnel from accessing the system.
7. Enclosures of stationary battery systems shall comply with the IBC. When stationary batteries are installed in separate equipment room accessible only to authorized personnel, they shall be permitted to be installed on an open rack for ease of maintenance.
8. Spill control and a means of spill response shall be provided.
9. An approved method of control and cleaning up the spill shall be provided.
10. Ventilation shall be provided in accordance with the IMC. Ventilation systems shall ventilate the floor area of the room at a minimum of 1 cfm/sq. ft. and shall be provided on a continuous basis.
11. The ventilation system shall be designed to limit the maximum concentration of Hydrogen 1% of the total volume of the room.
12. Temperature Control shall be provided to maintain safe operating conditions of the batteries.
13. Signs and placards shall be appropriately posted.
14. Seismic protection shall be provided for the battery storage system in accordance with the IBC.
15. Approved smoke detection shall be provided.
608.6.3 Mechanical ventilation systems shall be supervised at an approved central proprietary or remote station service or shall initiate an audible and visual signal at a constantly attended on-site location.
ATTENTION ****** THIS IS REQUIRED TO BE COMPLIANT WITH CODE
*** This section requires the supervision of both the required room and cabinets ventilation where mechanical systems are employed to provide notification of a system failure--to provide warning and reduce hydrogen concentration to build to hazardous levels.|
|FYI||Stationary Battery Systems IFC 2009, SECTION 608
Stationary storage battery systems having an electrolyte capacity of more than 50 gallons for flooded lead-acid, nickel cadmium (Ni-Cd) and valve-regulated lead-acid (VRLA), or 1,000 pounds for lithium-ion and lithium metal polymer, used for facility standby power, emergency power or uninterrupted power supplies shall comply with section 608 and Table 608.1.|
|FYI||CHEMICAL INVENTORY, AS DECLARED
INTERIOR UPS ROOMS A & B
132.5 gallons electrolyte UPS ROOM A
132.5 gallons electrolyte UPS ROOM B
DIESEL FUEL FOR GENERATORS
ONE, 1000 GALLON DIESEL FUEL INTEGRAL SUBBASE AST
( REMOVAL OF EXISTING 500 GALLON GENERATOR)
SETTING TEMPORARY GENERATOR ON SITE FOR TRANSITION 400 GALLON (ON SKID)
****This facility exceeds the hazardous materials permit amount threshold for flammable and combustible liquids, and electrolytes, therefore, this facility is required to apply for a CSFD Annual Operational Hamish Permit @ the CSFD website HAMISH @ http://csfd.springsgov.com/hamish/.
This facility will require a Hazardous Materials permit inspection for:
** Annual Operational Hazmat Permit (annual, automatically renewed by CSFD, fees apply
To schedule your Hazmat Inspections-- please contact the Divsion of the Fire Marshal @ 719-385-5978.|
|Attention||NOTE: THE DISAPPROVED TANK SUBMITTAL AND REVIEW SHALL NOT HOLD OR DELAY THE APPROVED SET OF BUILDING CONSTRUCTION PLANS & PERMITTING FOR THIS PROJECT. HAZMAT REVIEW HAS BEEN COMPLETED AND APPROVED ASSOCIATED WITH THE BUILDING CONSTRUCTION.
|Attention||Equipment, machinery, and required detection and alarm systems associated with the use, storage, or handling of hazardous materials shall be listed or approved. This requirement is subject to verification at the time of the Hazardous materials Inspection prior to signing the Fire Final.
THIS INCLUDES THE BATTERY & VENTILATION SYSTEMS. |
|FYI||Labeling - An NFPA 704 compliant Hazard Placard is required for each pedestrian entry door rooms containing hazardous materials in excess of the exempt amounts (this door could be interior or exterior) and all such doors shall be included. The minimum size of the Hazard Placard shall be 15" by 15". This requirement is subject to verification at the time of the Hazardous materials Inspection prior to signing the Fire Final.
Doors into electrical equipment rooms or buildings containing stationary battery systems shall be provided with approved signs. The signs shall state that:
1. The room contains energized battery systems.
2. The room contains energized electrical circuits.
3. The battery electrolyte solutions, where present, are corrosive liquids.|