||FYI||*****(STANDARD COMMENT) This project is: Woodmen Ridge Apartments, Maintenance Garage, 5628 Woodmen Ridge Vw: maintenance shop
Date of Plans: 9.28.12
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.
|Disapproved||*****(STANDARD COMMENT 19) DISAPPROVED COMMENTS
The following information and/or corrections are needed prior to completing a full plan review. Please respond, in writing on letterhead, to each of the following comments:
1. What is the occupancy classification - CSFD is unable to perform any sort of review without this information. Is it an S-occupancy? See additional comment regarding S-occupancies. Is it an F-occupancy? See additional comment on F-occupancies.
What will be stored within this building - is this for grounds maintenance? Will there be any flammable or combustible liquids stored in this building?
Also review the disapproved plans for additional written comments prior to submittal of new plans.|
|Disapproved||(STANDARD COMMENT) WATER PLANS
The City APPROVED" fire hydrant and water main plans are to be ATTACHED to all sets of construction plans for CSFD plan reviews.
|Disapproved||(STANDARD COMMENT) TEMPORARY ADDRESS
A temporary address has been assigned to these plans. CSFD will not approve the construction plans until the Regional Building Department Enumerations Office has assigned a permanent address to this facility, and has approved the construction plans. |
|Disapproved||(STANDARD COMMENT) HAZARDOUS MATERIALS:
Provide an inventory list, including their uses and amounts, for all chemicals and/or compressed gases, stored, handled and/or dispensed on site.
Provide listed information on the haz-mat permit amount certification form for all Use/Dispensing/Storage of Hazardous Materials and Flammable Liquids that will be used within this facility.
PLEASE INSURE YOU ANSWER ALL QUESTIONS AT THE BOTTOM OF THE FORMS, AND FILL OUT THE REQUESTED INFORMATION.
All forms and packets are available at http://www.springsgov.com/Page.aspx?NavID=1094.|
|Disapproved||(STANDARD COMMENT) 'F' OCCUPANCIES
Provide a detailed explanation of the products being manufactured, the process you use to fabricate your product, the products and components used to make the items that are manufactured.
If there are hazardous materials used for this process, provide detailed information as is listed in our haz-mat HMMP requirements. What materials are stored within the structure, how they are stored, the heights the products are stored at, etc. The better the explanation, the easier it is for us to review and approve the plans. |
|Disapproved||(STANDARD COMMENT) 'S' OCCUPANCIES
Provide a detailed explanation of the exact types of work being done in this facility. Clearly state if there will be welding, or automotive repair within this facility.
If there are hazardous materials used for this process, provide detailed information as is listed in our haz-mat HMMP requirements. Fill out and submit our "Hazardous Materials Permit Amount Certification Form." Your haz-mat must be under the exempt amounts for this facility to be considered as a S occupancy. |
|FYI||(STANDARD COMMENT) CORRECTIONS
All corrections and comments are to be submitted back to CSFD in writing, or provid submittal sheets/drawings, etc as requested, to complete the review. Corrections are not accepted over the phone, via fax or verbally.
|Attention||(STANDARD COMMENT) THE DISAPPROVED ITEMS MAY NOT CONSITITUE A COMPLETE LIST OF VIOLATIONS.
IT IS THE RESPONSIBILITY OF THE DESIGNER/ARCHITECT TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE ADOPTED CODES/STANDARDS AND INCORRECT INFORMATION PRIO TO RESUBMITTING.
|FYI||(STANDARD COMMENT) RESUBMITTALS
Re-reviews may be submitted back to the CSFD by direct submittal at the Construction Services counter, or through the Regional Building Department's routing system.
|FYI||(STANDARD COMMENT) REVIEWS
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirements are met as established by the Authority Having Jurisdiction, whether or not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the adopted fire code requirements, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.