||FYI||Freddys Frozen Custard 511 Garden of the Gods Rd Addition and Remodel
CN:Code: 09 IBC - 09 IFC - 11 PPRBC /Class: A-2 / Const: V-B /Stories: 1 /Size: 2697 /OL: 98
FH:Required Flow: gpm /# Hydrants /On site flow:
Additional comments: CO2; 1 mini bulk at 500 lbs EXTERIOR STORAGE
Hazmat review: 500 lb Carbon Dioxide vessel for beverage dispensing
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.
|FYI||This facility will store and fill the CO2 container on the exterior of the restaraunt adjacent to the building as shown on plan sheet A1
***See redline comment for vehicle protection as noted per IFC 2009 Section 312
Please add Bollards due to the potential for the drive through vehicles at this location.
|FYI||ONE, 500 lb CARBON DIOXIDE VESSEL (CO2)
4370. CUBIC FEET
CHART INDUSTRIES is the supplier
NFPA = 1-0-0 special = SA
TLV-TWAs, 5000 ppm (ACGIH, 2004)
TLV-TWA 15 MIN STEL 30,000 ppm
High Pressure liquid and gas. Can cause rapid suffocation....CO2 IS AN ASPHYXIANT
May cause frostbite.
****** ATTENTION *******
Indoor storage of compressed gases falling into categories such as asphyxiants, irritants can be hazardous regardless of the type of gas involved simply due to the hazards related to asphyxiation.
****THIS IS AN OUTDOOR INSTALLATION
NOTE: Storage areas where an accumulation of inert gas could occur should be continuously monitored with an appropriate alarm system to indicate an oxygen deficient atmosphere. (Recommended)
|Attention||ATTENTION EXTERIOR STORAGE REQUIREMENTS:
**Compressed gas containers, cylinders and tanks, whether full or partially full, shall not be exposed to artificially created high temperatures exceeding 125°F or sub-ambient (low) temperatures unless designed for use under the exposed conditions.
** Areas used for the storage, use and handling of compressed gas containers, cylinders, tanks and systems shall be secured against unauthorized entry and safeguarded in an approved manner.
** Compressed gas containers, cylinders, tanks and systems which could be exposed to physical damage shall be protected. Guard posts or other approved means shall be provided to protect compressed gas
containers, cylinders, tanks and systems indoors and out-doors from vehicular damage and shall comply with IFC 2009 Section 312.
** Labeling - An NFPA 704 compliant Hazard Placard is required for each pedestrian entry door rooms containing hazardous materials in excess of the exempt amounts (this door could be interior or exterior) and all such doors shall be included. The minimum size of the Hazard Placard shall be 15" by 15". This requirement is subject to verification at the time of the Hazardous materials Inspection prior to signing the Fire Final.|
Facilities shall declare the storage and use of small Insulated Carbon Dioxide Systems used in Beverage Dispensing.
Gaseous Carbon Dioxide is an asphyxiant gas and exposure to high concentrations may cause toxic effects including asphyxiation. To provide for the safety of building occupants and emergency personnel, ventilation in accordance with the IFC Sections 3007.2, 2704.3 or 2705.1.9 is required where concentrations of this gas are stored or present.
All new or proposed building ventilation system designs shall submit for review and permit approval to the Pikes Peak Regional Building Department.
THIS IS AN OUTDOOR INSTALLATION|
|Attention||THE CHEMICAL INVENTORY, AS DECLARED, DOES NOT EXCEED THE ALLOWABLE THRESHOLDS FOR THE ANNUAL HAZARDOUS MATERIALS OPERATIONAL PERMIT.
500 LB CO2 (inert/asphyxiant = 4370 scf ********** (permit threshold = 6,000 cf)
*** This facility is NOT required to apply for the Annual Hazardous Materials Operational Permit at the CSFD
*** To Schedule the hazardous materials construction inspection FOR THE CERTIFICATE OF OCCUPANCY FINALS please contact the Division of the Fire Marshal @ 719-385-5978.
*** For further questions or information please contact the Division of the Fire Marshal main number at 719-385-5978. |
|Attention||LABELING AND MARKING
** Stationary compressed gas containers, cylinders and tanks shall be marked with the name of the gas Markings shall be visible from any direction of approach.
** Portable compressed gas containers, cylinders and tanks shall be marked in accordance with CGA C-7.
Piping systems shall be marked in accordance with ANSI A13.1.
** Markings used for piping systems shall consist of the content#s name and include a direction-of-flow arrow.
** Markings shall be provided at each valve; at wall, floor or ceiling penetrations; at each change of
direction; and at a minimum of every 20 feet or fraction thereof throughout the piping run.
Portable containers, cylinders and tanks. Portable compressed gas containers, cylinders and tanks shall be
marked in accordance with CGA C-7.
Signs clearly establishing the location and identity of shut-off valves are to be provided.
All inert piping systems shall be identified by appropriate labeling with the name of the gas.
Warning signs shall be posed at each entrance to the room or enclosure where the bulk inert gas system is installed. Wording shall include:
WARNING ---(name of gas)
HIGH CONCENTRATION OF GAS MAY OCCUR
IN THIS AREA AND MAY CAUSE ASPHYXIATION.
VERIFY THAT OXYGEN CONCENTRATION IS ABOVE 19.5% BEFORE ENTERING
AND DURING ACTIVITY IN THIS AREA.|
|Attention||Piping shall be protected against physical damage.
Signage shall be provided for piping and hose systems as follows:
1. Above-ground piping systems shall be marked in
accordance with ANSI A13.1.
2. Station outlets shall be marked to indicate their intended
3. Signs shall be posted, indicating clearly the location and
identity of section shutoff valves.|
|FYI||Labeling - An NFPA 704 compliant Hazard Placard is required for each pedestrian entry door rooms containing hazardous materials in excess of the exempt amounts (this door could be interior or exterior) and all such doors shall be included. The minimum size of the Hazard Placard shall be 15" by 15". This requirement is subject to verification at the time of the Hazardous materials Inspection prior to signing the Fire Final.|
|Attention||NOTE TO CONTRACTOR & FIRE INSPECTOR: Prior to scheduling the Fire Final please contact the Hazardous Materials Inspector to arrange a Hazardous Materials Inspection prior to final signature being provided.|
|FYI||Equipment, machinery, and required detection and alarm systems associated with the use, storage, or handling of hazardous materials shall be listed or approved. This requirement is subject to verification at the time of the Hazardous materials Inspection prior to signing the Fire Final.|
|FYI||A minimum of 1 set of Material Safety Data Sheets (MSDS), hard copy, must be readily availiable on the premises at all times.|