||FYI||*****(STANDARD COMMENT 1) This project is: Pho Nomenal, 5825 Stetson Hills Bl, Suite 100: Interior finish - restaurant
Date of Plans: December 12
|FYI||(STANDARD COMMENT 3) HEAD EXTENDERS:
BE ADVISED: Head Extenders are not allowed in the City of Colorado Springs effective Immediately. 1/08|
|FYI||*****(STANDARD COMMENT 6) The fire sprinkler system is being installed by: SIMPLEXGRINNELL
This plan review is based on the requirements found within the adopted International Building Code, International Fire Code, and the 2010 editions of NFPA Standard 13, 13R or 13D as applicable.
CSFD does not allow any combustibles into a building until a sprinkler system has passed it's final acceptance test performed by CSFD Inspector's.|
|FYI||*****(STANDARD COMMENT 8) SCOPE OF WORK:
Area/scope of work is 31----- SPRINKLERS IN SUITE 100----of the building.
Flex Connections: NOT PERMITTED
|FYI||(13) ELECTRICAL SUPERVISION REQUIRED:
All valves controlling the water supply for automatic fire sprinkler systems, fire pumps, tanks, water levels and temperatures, critical air pressures, and water flow switches on all sprinkler systems shall be electrically supervised. (2003 IFC 903.4)
An approved central station, remote station or proprietary supervising station as defined by national standards shall monitor this supervision.
PLEASE NOTE - Separately Fire Department approved plans and permits are to be obtained prior to the installation of the required sprinkler system monitoring system or fire alarm system.
A Knox Box is also required. Contact the CSFD for the information needed to order this key box.|
|FYI||(13) STOCK OF SPARE SPRINKLERS:
A spare sprinkler head box shall be provided and shall contain not less than 6 spare sprinklers. A minimu of 2 sprinkler of each type and temperature rating shall be provided. It shall also contain the sprinkler wrenches need to replace the heads.
A list of the sprinklers installed in the property shall be posed in the sprinkler cabinet. The list shall include the following information:
a) Sprinkler ID Number
b) General description of the sprinkler
c) Quanitity of each type of sprinkler contained in the cabinet
d) Issue or revision date of the list.
|FYI||(STANDARD COMMENT 10) INSPECTIONS
Due to the dynamic nature of inspectors schedules, PLEASE call your inspection requests in with ample time to allow scheduling.
When calling, please have your complete CSFD plan review number(s) ready for each inspection request.
( i.e. 20001234 - HM -2 or 20000012 - CN - 1)
The CSFD Approved sets of plans are to be on site for all inspections.|
|Attention||(STANDARD COMMENT) SCHEDULING INSPECTIONS:
Please call 719-385-5982 and choose option 2 to schedule all construction related inspection activities.
|FYI||(STANDARD COMMENT 37) ROUGH VISUAL INSPECTIONS:
Rough Visual inspections shall be completed PRIOR TO any bucket tests or final inspections.|
|FYI||(STANDARD COMMENT 38) CONCEALED WORK:
The fire sprinkler piping shall not be covered up by walls, sheetrock, ceiling tiles, etc... prior to the CSFD visual inspections of the piping. If the piping is covered, and the inspectors cannot inspect it as is required by Fire Code, the walls,sheetrock, ceiling tiles, etc... will be required to be removed. If this means that finished ceilings will need to be removed, this will be required to be done!
|FYI||(STANDARD COMMENT 39) PLAN REVIEW/PERMIT FEES:
All fire department fees are to be paid prior to issuance of any permits. These fees must be paid directly to the Colorado Springs Fire Department - Development Review Enterprise - at 2880 International Circle - Suite 200-7. |
|FYI||(STANDARD COMMENT) REVIEWS:
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirement are met as established by the Authority Having Jurisdiction, whether of not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the fire code requirements of the 2003 International Fire Code, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.