NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
UCH MEMORIAL HEALTH CENTRAL MAIN
01400 BOULDER ST
||Disapproved||*****20-HEAD LETTER DISAPPROVALS
--XX---Multiple letters have been submitted for this scope of work/building permit, thus the total modifications exceed 20-heads.
-----Your company is currently restricted from use of this privilege through a ruling from Fire Board of Appeals.
-----Your company is currently not licensed to perform work on fire suppression systems, please contact Contractor Licensing at 719-327-2880 to correct this.
-----This system modification does not qualify for use of the 20-head letter privilege; i.e. special hazard (paint booth), pipe schedule.
-----The information you have provided is not complete, please provide the following:
-----This building permit encompasses work on two levels including permanent walls - please clarify the scope of this work and if there is additional work on the other levels
-----A building permit is required for the construction work associated with this work.
||Approved||Per telcon with Phil Valdez this date @ 1600 hours, the work was never done in June and he was not aware that a previous letter had been done. Per his direction, this letter was an unnecessary duplication.|
||FYI||***** 20-HEAD LETTER:
Date Submitted: 06/26/12
Total number of heads affected : 7
Location of work: Basement Breakroom
Bldg permit #:I24687
Flex Connections approved in this facility?: NO
Brand: if known
Equivalent Length: if known
UL 2443/FM 1637 Complaint:|