NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
00590 UNION BL
||FYI||This project is: U S Olympic Training Center, Entry Control Point, 590 N Union Bl: new security station
Date of Plans: 5.15.12
ABOVEGROUND STORAGE TANK INTEGRAL WITH GENERATOR
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.
|Disapproved||Diesel storage tank and generator will require a aboveground storage tank installation permit and a separate plan/permit review under separate cover/deferred submittal. Amount/size of tank was not reported?
The CSFD requires a Construction Permit for the installation of any aboveground fuel tank in excess of 60 gallons. Flammable and combustible liquids shall comply with the IFC 2009 CHAPTERS 34, 22 AND 27 as amended, and NFPA 30. It is the responsibility of the TANK INSTALLER to submit an application for the tank installation permit prior to installation.
The tank installer shall submit permit application forms and documents to :
CSFD Office of the Fire Marshal
375 Printers Parkway
A full set of the tank manufacturer's cut sheets, a declaration of contained volume, a declaration of tank contents and a to scale site plan of the tank location with respect to walls, other structures, property lines, drive lanes, etc. Exterior tanks will be required to have vehicular protection diagrammed and installed in accordance with the 2009 IFC, Chapter 3, section 312. Any associated piping shall be diagramed and submitted as well.
***PERMIT APPLICATION FORMS WERE NOT SUBMITTED WITH THE DOCUMENTS.
COMPLETE THE CSFD AST INSTALLATION FORMS AND RESUBMIT TO THE CSFD (DEFERRED SUBMITTAL)
PERMIT APPLICATION FORMS CAN BE OBTAINED ON THE CSFD WEBSITE http://www.springsgov.com/page.aspx?navid=1094
Failure to apply for permit prior to work may be subject to work without permit additional fees. |