NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
7 ELEVEN STORE CORPORATE NO 35338
00330 ACADEMY BL
||Attention||From: Michael Ornelas [mailto:email@example.com]
Sent: Thursday, March 28, 2013 10:00 AM
To: Yeager, Kay A.
Cc: Wrobel, Julie; 'Alysa Miller'; 'Nolte, Christopher - Bovis Lend Lease'
Subject: RE: #35338 7-Eleven 330 S. Academy, Colorado Springs, CO.
Good Morning Kay,
I wanted to advise you and Jay Weightman that upon completing the original scope of work below (see way down at the bottom of this trail), we could not get the secondary piping to hold air as required to pass inspection. It has been decided to re pipe the entire site in efforts to avoid more lost time. Therefore, we will keep the UDC's that we already installed and re pipe back to the tank area and utilize the existing STP containments. I wanted to advise you of the changes so that Jay would be fully aware of what to expect when he returns to inspect. He has probably wondered why we have not contacted him since he came to visit us the first time. We have advised the State O.P.S. of the change and we have submitted the application attached to them for approval. Please review the items attached and we look forward to our scheduled inspection which we anticipate to be in about two weeks.
Please feel free to contact me if you have any questions. Thanks
Revised Scope of work:
1.) OVERSEE THE SAW CUTTING AND EXCAVATION OF THE NEW PROPOSED TRENCHES PER THE SKETCH AND THE TANK HOLE.
2.) ONCE THE TRENCHES AND TANK AREA HAVE BEEN EXCAVATED, WE WILL BEGIN THE PROCESS OF RE PIPING THE NEW PIPING TO CONSIST OF 3" OVER 2" A.O. SMITH FIBERGLASS PIPING.
3.) UPON COMPLETION OF GLUING THE PRIMARY PIPING AND CURING, WE WILL AIR TEST AND WILL HAVE ALREADY PRE PLANNED AND SCHEDULED AN INSPECTION FROM THE STATE.
4.) ONCE INSPECTION HAS PASSED, WE WILL BEGIN THE PROCESS OF PIPING THE SECONDARY PIPING AND CURE THE PIPE FOR A PRE PLANNED AND SCHEDULED INSPECTION FROM THE COLORADO SPRINGS FIRE DEPARTMENT.
5.) ONCE ALL INSPECTIONS HAVE BEEN SATISFIED, WE WILL BACKFILL THE TRENCH AREAS AND THE TANK AREA AND PROCEED TO OVERSEE THE PREPING OF THE TRENCHES FOR POURING CONCRETE.
6.) WE WILL OVERSEE THE POURING AND FINISHING AS PREVIOUSLY PLANNED IN ALL OF THE CHANGE ORDERS.
7.) CLEAN UP ALL OF THE CONSTRUCTION DEBRIS.
Michael A. Ornelas
Kubat Equipment & Service
SEE ADDITIONAL ELECTRONIC DOCUMENTS 4/2/13 KAY THAT ACCOMPANY THIS SCOPE OF WORK.
||FYI||7 Eleven, 330 S. Academy Boulevard
CN:Code: IBC - IFC - PPRBC /Class: / Const: /Stories: /Size: /OL:
FH:Required Flow: gpm /# Hydrants /On site flow:
DV:Proposing to demo the existing Conoco and build new 2010sf convienece store with fuel pumps.
INSPECTOR SEE ELECTRONIC DOCUMENTS!
CORRODED CONDUIT REPLACEMENT FOR UDCs
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.
|FYI||3403.6 Piping systems. Piping systems, and their component parts, for flammable and combustible liquids shall be in accordance with Sections 3403.6.1 through 3403.6.11.
3403.6.1 Nonapplicability. The provisions of Section 3403.6 shall not apply to gas or oil well installations; piping that is integral to stationary or portable engines, including aircraft, watercraft and motor vehicles; and piping in connection with boilers and pressure vessels regulated by the International Mechanical Code.
3403.6.2 Design, fabrication and installation of piping systems and components. Piping system components shall be designed and fabricated in accordance with the applicable standard listed in Table 3403.6.2 and Chapter 27 of NFPA 30, except as modified by Section 3403.6.2.1.
|FYI||Please contact the CSFD DFM @ 719-385-5978 to schedule the hazardous material inspection for this project. Your Inspector is Jay Weightman. |
|FYI||Documents provided included listed equipment, photos, scope of work, |