NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
NOODLES AND COMPANY STORE 159
02455 MONTEBELLO SQUARE DR
||FYI||***** 5-DEVICE LETTER:
Date Submitted: 11/29/12
Date of Work: 11/30/12
Contractor: Safe Systems
Scope : Relocate interior horn/strobe due to tenant finish
Current Draw: 4.14 AH
Battery Size: 12V/7AH
Location of work: Tenant Space
Bldg permit #: I43189
NOTE: THIS LETTER APPROVED WITH MIKE MAAG AS RME PER TELCON WITH KCOOPER 11/29 1559
||Disapproved||***** 5-DEVICE LETTER DISAPPROVALS:
-----Multiple letters have been submitted for this scope of work/building permit, thus the total modifications exceed 5 devices.
-----Your company is currently restricted from use of this privilege through a ruling from Fire Board of Appeals.
-----Your company is currently not licensed to perform work on fire suppression systems, please contact Contractor Licensing at 719-327-2880 to correct this.
---XX--The information you have provided is not complete, please provide the following:
Larson is shown as the NICET for this company and must sign submittals
A drawing is required (8.5 x 11)
A battery calc is required (or statement in letter that no change will occur with this work)
Letters must be submitted a MINIMUM of 2 business days prior to start of work
(Does not include weekends or City Holidays)
A Fire Alarm Permit Application must be included (2 pages)