NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
||Approved||this scope of work is to relocate a hydrant in the close out of hangar E9.|
||FYI||*****(STANDARD COMMENT 1) This project is: Colorado Springs Business Airpark Hangar Complex , Hangar E12
Date of Plans: 2.26.13
You can access our web site for the latest fire department plan review comments:
1. From www.pprbd.org, select PLAN REVIEW then FIND PLANS next COLORADO SPRINGS
2. Scroll down to the correct address. You may then select APPROVED/DISAPPROVED to view comments associated with that particular project.|
|FYI||*****(STANDARD COMMENT) SCOPE OF WORK:
|Disapproved||(DISAPPROVED) BUILDING DATA
The "BUILDING DATA" information must be provided for each building, and should be indicated inside the footprint layout of the building, or just next to the footprint, and on each of your plan sheets that are to be signed by CSFD:
Please refer to our Water Supplies Information packet for the required information/template.|
|Disapproved||(DISAPPROVED) FIRE FLOW REPORT
Provide confirmation on the fire flow results from Colorado Springs Utilities. A copy of their report for this area is required to be provided with your plan submittals.
When multiple fire flows are provided from CSU, please indicate all flows on your submitted plans.
NOTE - To request a fire flow report, please go to: http://www.csu.org/business/businesswithus/documents/item10501.pdf
|FYI||(STANDARD COMMENT) REVIEWS:
Colorado Springs Fire Department construction reviews are based upon information provided on the drawings and/or the attached reference material. Issues or features that are not presented within the construction documents are assumed to be complaint with applicable codes/standards. It is the responsibility of the building owner to ensure that minimum code requirement are met as established by the Authority Having Jurisdiction, whether of not the requirements are specifically indicated on the submitted construction documents.
The CSFD has reviewed the submittal in accordance with the fire code requirements of the 2003 International Fire Code, CSFD local amendments, City Code Standards, and applicable NFPA Standards. All plan review comments are subject to final on-site field inspections, and testing by the CSFD. Review and approval by the CSFD shall not relieve the applicant of the responsibility of compliance with the International Fire Code.