NOTE - THE NOTED DISAPPROVED ITEMS MAY NOT CONSTITUTE A COMPLETE LIST OF VIOLATIONS. THE DESIGNER IS TO CONDUCT A COMPLETE RE-REVIEW OF THE PLANS FOR ADDITIONAL VIOLATIONS OF THE STANDARD COMMENTS AND INCORRECT INFORMATION PRIOR TO RESUBMITTING.
System plans must be picked up within 30 days. All system plans left longer than 30 days will be discarded as abandoned.
All corrections were addressed. Plans are approved|
|Attention||***HYDRANTS: COMMERCIAL BUILDING DATA:
Size of Structure -6200- sq ft
Type of construction -VB-
Fire Sprinklers System Y-- N-XX-
Area Separation Walls (ASW) being installed Y-- N-XX-
Largest area formed from ASW --
Required GPM: -2000- gpm
Number of hydrant(s) required: -2-
Required AVG spacing between hydrants: -450- ft
Required hose lay: -225- ft
Max designed distance from hydrant to within 150 ft of all portions of bldg 1st floor: -100- ft
(distances measured as the fire truck would drive on HS-20 load bearing - asphalt or concrete roads)
On site theoretical fire flows are -2200 - 3000- gpm where -2000- gpm required
Is this a simultaneous flow? Y -- N -XX- Number of hydrants flowing -- Flows:
On site number of hydrant(s) are -2- where -2- are required
Are hydrants blocked by parked vehicles, fences, walls, etc? Y -- N -XX-
Are hydrants at the end of DEAD-END STREETS? Y -- N -XX-
Is this a HILLSIDE AREA - MAX SPACINGS 300' & 150'? Y -- N -XX-
NEED MODELED fire flow data? Contact - Colo. Spgs. Utilities (CSU) - Keta Donegan @ 668-8733, FAX 668-5651 - she will provide MODELED flow report information to you. |
||FYI||This project is: Villages at Wolf Ranch, Phase 3, located northeast of Wolf Center Drive and Leon Young Drive. Proposing 73 single family dwelling lots.
FH1: 26 lots, East of Wolf Center Drive, South of Fergus Drive, West of Boylston Drive, North of Leon Young Drive
DV: FN-1= CPC FP 06-023 - Village at Wolf Ranch Filing 16.
ATTENTION: See our web site for our latest plan review comments for your job at:
www.springsgov.com - go to "City Agencies" (tab on the teal bar to get a drop box) - click on - "Fire Department" - (Using the links down the left side of the page), click on - "Web Guide." Once you're into the Web Guide, click on "Plan Review Status" This will also give you access to numerous other items that may assist you in your future project design work.
1) Provide CSFD with a copy of the plans at the time of final review
2) Add Plan Review number 2006-0161 FH 1
3) Return ALL redlined plans
4) Add flow data on the plan
5) Provide CSU fire flow data
|FYI||Please return ALL of the exact red lined plans we have previously reviewed for all re-reviews of this project.|
|FYI||RJG If you have any specific questions or concerns about these comments, please feel free to contact me at:
Fire Protection Engineer 1
Colorado Springs Fire Department
Development Review Enterprise
Fire Prevention Division
2880 International Circle - Suite 200
Colorado Springs, CO 80910